Pellet boiler Defro ALFA II 12 | 17 kW (eligible)

2025-04-16T12:24:49+02:00

Vendor: Defro
Type: Pellet boiler
Price: 9499.00 - 10658.00 (4 variants)

Nationwide commissioning and Assembly via customer service upon request Possible! Delivery is made by truck with a liftgate. to the curb!
The boiler meets the requirements of BlmSchV2 and possesses CE Declaration of Conformity.

ALFA II – Pellet boiler with central pellet burner, first-class features for maximum heating and operating comfort

Features of the Alfa II

The Defro Alfa II features a compact boiler design with optional expansion of the pellet hopper volume (PLUS version).

Standard features include automatic heat exchanger cleaning and ash removal.

Central pellet burner for efficient fuel combustion. Automatic burner cleaning ensures reliable boiler operation.

TSS Twin Spark System – two alternately activated ignition elements.

Ceramic baffle plates above the combustion chamber. Vertical tube heat exchangers with turbulators for maximum energy efficiency.

Vacuum sensor to ensure the necessary vacuum in the combustion chamber.

Powerful induced draft fan for the necessary negative pressure in the boiler and stabilization of combustion.

Intuitive and very easy operation of the boiler thanks to the modern APC Center control unit with touchscreen, which operates 6 pumps and two heating circuit mixers and is equipped with a factory-installed internet module.

A professional boiler connection package including return temperature boost and boiler circulation pump is included.

Level sensor in the pellet container to indicate the fuel reserve and to interrupt operation so that the auger does not run dry.

Optionally, a lambda sensor can be retrofitted, making combustion even more efficient and environmentally friendly.

Control of the Defro Alfa II

APC Center control unit with touchscreen, which operates 6 pumps and 2 heating circuit mixers,

Standard with built-in internet module

Scope of delivery

Touchscreen APC CENTER, APC CENTER control panel

Internet module,

PID function,

Weather-compensated heating circuit control,

TSS automatic ignition system,

Automatic pellet burner Cleaning,

Hydraulic set with return flow boost and boiler circulation pump,

Adjustable feet

Accesories

GSM module,

Module I-1,

Module I-1M,

Lambda sensor with module ST-69,

Internet module WIFI

Room thermostat ST-292 v3,

Room thermostat ST-292 v2,

DEFRO SPK Lux room thermostat

Wireless room thermostat SPK LUX,

Set for wireless RS communication, version PLUS – enlarged container

Technical specifications of the Defro Alfa II

Alfa II 12 kW

Rated power: 12 kW

Power range: 3.2 - 12.2 kW

Fuel: Pellets ø 6 mm

Efficiency full load/partial load: 90.7%/91.2%

Energy efficiency class: A+

Pellet hopper capacity Standard/Plus: 85/145 kg

Maximum permissible operating pressure: 3 bar

Required chimney draft: 8 Pa

Exhaust gas temperature: 106 °C

Exhaust gas mass flow: 9 g/s

CO2 content: 10.7%

Boiler weight Standard/Plus: 357/372 kg

Alfa II 17 kW

Rated power: 17 kW

Power range: 4.9 - 17.1 kW

Fuel: Pellets ø 6 mm

Efficiency full load/partial load: 90.7%/91.2%

Energy efficiency class: A+

Pellet hopper capacity Standard/Plus: 85/145 kg

Maximum permissible operating pressure: 3 bar

Required chimney draft: 10 Pa

Exhaust gas temperature: 119 °C

Exhaust gas mass flow: 13 g/s

CO2 content: 11.2%

Boiler weight Standard/Plus: 373/390 kg

Pellet heating is a better alternative in many existing houses

Heating with pellets or a heat pump?

The choice between a pellet boiler and a heat pump depends on various factors, including individual needs, the specific conditions of the property, and economic considerations. The budget for a new heating system in an older building often doesn't allow for a heat pump, as the initial investment is linked to several subsequent costs. Whether radiators need replacing, the house needs insulation, or a photovoltaic system needs to be installed for the heat pump to operate efficiently, the costs increase significantly and may not be cost-effective in many existing homes in the long run. Pellet boilers can be integrated more easily and economically into an existing heating system, keeping the initial investment moderate. Our modern boilers are highly efficient and provide consistent heat output regardless of outside temperatures. It's advisable to speak with one of our sales consultants to determine the best option for your home.

A pellet boiler works similarly to a gas or oil boiler, but uses wood pellets as fuel.

The pellets are conveyed to the burner via an auger, where they are burned to generate heat. This heat is then passed through a heat exchanger, which heats the water in the heating system.The heated water is then piped to the radiators or underfloor heating systems in the house to heat the rooms. An electronic control system ensures that a sufficient quantity of fuel is transported to the burner and that the combustion air supply is automatically regulated to maximize efficiency.

Environmental friendliness: Wood pellets are a renewable fuel and have a low CO2 footprint compared to fossil fuels such as oil or gas.

Efficiency: a pellet boiler is very efficient and can convert up to 95% of the fuel into heat.

Cost savings: Wood pellets are generally cheaper than oil or gas; you can save money in the long term with our pellet boilers.

Convenience: Pellet boilers operate automatically, and some models are fully automatic and require very little intervention.

Pellet boilers and environmentally friendly heating!

From the perspective of "environmentally friendly heating," pellet and wood-burning heating systems remain an excellent choice. Burning wood releases as much carbon dioxide as it absorbs during its growth. It is therefore considered a climate-neutral fuel. Wood is a constantly renewable and thus sustainable resource. Our wood and pellet boilers have therefore been designed in accordance with current emission guidelines and comply with the strict regulations of the German Federal Immission Control Act (BImSchV).

Download

Datasheet