Keyon split air conditioning YAA1FB6 with frost protection function

2025-04-16T12:26:00+02:00

Price: 705.50 - 1445.00 (4 variants)

Keyon Series Air Conditioner

Highlights of the air conditioning system

Energy efficiency class A++/A+

“I FEEL” function

"8 °C Frost Protection" function

New design of the outdoor unit

Includes infrared remote control

Hidden display

Includes cold plasma ionizer

Integrated WiFi control

Lamella movements:

- 2.7 kW and 3.2 kW horizontal

- 4.6 kW and 6.2 kW horizontal

vertically adjustable

OPTIONAL: MODBUS control via SWC-02 or SWC-04 (except SIH-09BIK) is possible

The Keyon air conditioner is a true all-rounder among SINCLAIR split wall units.

Thanks to a wide range of features and an attractive price/performance ratio, the series is becoming a sales hit.

Keyon Series Air Conditioner

The hidden display, which can be switched off if desired, always keeps you informed about the operating mode and target temperature.

Operation via smartphone is also possible after a one-time setup, giving you full control over your air conditioning system even when you're on the go.

The built-in cold plasma ionizer cleans your room air and creates a comfortable indoor climate.

Keyon Series Air Conditioner

The included infrared remote control further enhances the comfort of the Keyon series air conditioner, measuring, for example, the room temperature where you are and adjusting the output accordingly (the "I FEEL" function). The "8°C Frost Protection" function prevents your rooms from cooling down too much in winter; if the room temperature drops below 8°C, the unit activates an efficient heating mode.

Technical specifications: Keyon series air conditioner

Model | | | SIH-09BIK | SIH-12BIK | SIH-18BIK | SIH-24BIK
| | | SOH-09BIK2 | SOH-12BIK2 | SOH-18BIK | SOH-24BIK
Performance | Cool | kW | 2.7 (0.6 - 3.4) | 3.2 (0.9 - 3.7) | 4.6 (1.0 - 5.3) | 6.2 (1.8 - 6.4)
| Heat | kW | 2.8 (0.6 - 3.7) | 3.4 (0.9 -4.1) | 5.2 (1.0 - 5.7) | 6.5 (1.6 - 6.6)
Voltage/Frequency | | V/Ph/Hz | 220-240/1/50 | 220-240/1/50 | 220-240/1/50 | 220-240/1/50
Power consumption | Cool | kW | 0.74 | 0.99 | 1.36 | 1.77
| Heat | kW | 0.7 | 0.92 | 1.34 | 1.65
Max. power consumption | | kW | 1.5 | 1.5 | 1.9 | 2.2
Max.Operating current | | A | 7.5 | 7.5 | 9 | 10
SEER/SCOP | | | 6.6/4.2 | 6.5/4.1 | 6.4/4.0 | 6.8 /4.0
Energy efficiency class | Cooling/Heating | | A++/(A+/A+++/B) | A++/(A+/A+++/-) | A++/(A+/A+++/-) | A++/(A+/A+++/-)
Eta value | Cooling/Heating | | 261/165 | 257/161 | 253/157 | 241/157
Air volume flow | Inside | m³/h | 550/500/430/290 | 680/560/450/390 | 850/750/650/550 | 1100/950/750/650
| Outside | m³/h | 1950 | 1950 | 1950 | 2800
Sound pressure level at 1 m | IG/AG | dB(A) | 40/38/34/23/51 | 41/36/32/23/52 | 48/41/37/31/53 | 48/44/40/35/58
Sound power level | IG/AG | dB(A) | 55/48/44/36/62 | 57/46/42/37/64 | 58/51/47/34/63 | 61/58/53/49/67
Dehumidify | | l/h | 1.4 | 1.4 | 1.8 | 1.8
Refrigerant/Fill quantity | Type/Quantity | kg/Eq. CO2 | R32/0.53/0.36 | R32/0.57/0.38 | R32/0.75/0.51 | R32/1.30/0.88
Pipe diameter | Cool | inch/mm | 1/4/6.0 | 1/4/6.0 | 1/4/6.0 | 1/4/6.0
| Heat | inch/mm | 3/8/9.5 | 3/8/9.5 | 3/8/9.5 | 1/2/12.0
Min./Max. pipe length | | m | 3/15 | 3/15 | 3/25 | 3/25
Max.altitude difference | | m | 10 | 10 | 10 | 10
Pre-filled pipe length | | m | 5 | 5 | 5 | 5
Additional amount of cold | | g/m | 16 | 16 | 16 | 16
Dimensions (H x W x D) | Inside | mm | 251x770x190 | 289x849x215 | 300x972x225 | 325x1081x248
| Outside | mm | 550x732x330 | 550x732x330 | 550x732x330 | 555x873x376
Net weight | Inside | kg | 8.5 | 10.5 | 13.5 | 16.5
| Outside | kg | 25 | 25 | 26.5 | 36.5
Target temperature range | | °C | 16-30 | 16-30 | 16-30 | 16-30
Operating temperature range | Cooling/Heating | °C | -15~43/-15~24 | -15~43/-15~24 | -15~43/-15~24 | -15~43/-15~24
Includes remote control | | | INFRARED | INFRARED | INFRARED | INFRARED
Includes Wi-Fi module | | | YAA1FB6 | YAA1FB6 | YAA1FB6 | YAA1FB6
Includes catechin filter and activated carbon filter | | | SAF-OPWC4 + -A4 | SAF-OPWC4 + -A4 | SAF-OPWC4 + -A4 | SAF-OPWC4 + -A4

*Technical changes reserved | Images may differ